Re: Unexplained rebooting
Donovan Baarda wrote:
very OT, but I need to complain somewhere... I have problems _caused_ by a
Every night, the power here creeps just above 255V (should be 240V here in
Aus). This is enough to make my UPS complain and kick in. I have genpowerd
setup to wait 5 mins, then do a controlled shutdown, finally turning off the
Under normal powerfail situations, the UPS will turn the PC on when power
returns. However in this case the power doesn't actually go off, and the UPS
doesn't turn back on when the power creeps back down to normal levels in the
This means the UPS shuts my system down every night and it doesn wake up
until I manually powercycle the UPS. I suspect most UPS's would exibit this
kind of behaviour in this situation, as they would be designed to handle
power losses and brief surges, not long sustained overvoltages.
I've complained to the power companies, and after months of them stuffing
around with the power to no effect, I gave up and took off the UPS. The
system hasn't gone down since, but the power is still going above 255V every
Sounds like you need a better UPS. Some of the better brands are capable
of trimming the input voltage in cases like you describe, so that they
don't go on battery in high voltage situations (at least that's what the
sales literature claims).
Your UPS may also have a DIP switch to loosen the tolerance it imposes
on the input.
ETN Systems Inc.
2125 1st Ave East
Hibbing MN 55746